Cleanroom manufacturing processes require some of the cleanest water in the world. The most demanding applications are semiconductor manufacturing and pharmaceutical manufacturing which require “ultra-pure” water. The cleanroom water systems use multiple steps to create the water.
The typical cleanroom water system uses both reverse osmosis and deionizing systems.
Most cleanroom water systems start with a sediment filter to remove the largest particles, then a carbon filter to remove volatile organics.
The next step is the reverse osmosis system which removes up to 98% of impurities/contaminants in the cleanroom water. Reverse osmosis systems push water through the semipermeable membrane to filter out contaminants. Often there is a UV lamp in the water line to kill bacteria. Cleanrooms can use liquid monitoring systems that count particles in water to measure cleanliness after the reverse osmosis step.
Following reverse osmosis, the next step is a deionizing system to remove ions (minerals and salts) ed by passing the water over charged resin beds. The effectiveness of ion contaminant removal is measured by the resistivity of the water which can reach megaohms/cm. By comparison, tap water is typically 1000-5000 ohms/cm. In some cases the cleanroom water is purified even further by running over other chemical beds.
Another method of purifying water for cleanrooms is distilling water. By converting water into steam, you can remove the minerals and organic contaminants. Typical resistance of distilled water is 500,000 ohm/cm. It is an extremely energy intensive process. This is a less common cleanroom water system than reverse osmosis and deionization.
What is a Cleanroom Interlock?
All About Cleanroom Curtains and Strip Curtains
Difference Between Cleanroom Bench and Cleanroom Fume Hoods
All About Cleanroom Air Change Rates
All About LED Cleanroom Ceiling Lights
Stainless Steel in Cleanrooms - Which is the Best Grade?
All About Nutraceutical Cleanrooms
Differential Pressure in Cleanrooms Explained
Pass Thru Chambers in Cleanrooms
What is an ISO-5 Cleanroom Classification?
Top Seven Cleanroom Design Mistakes
Cleanroom Fan Filter Units vs Air Handling Units
Cleanroom vs. Controlled Environment
How Do Cleanroom Air Showers Work?
What is an ISO-7 Cleanroom Classification?
All About Cleanroom Sprinklers
ESD Environment Considerations for Cleanrooms
How the 2022 Chips Act Can Pay for Cleanrooms
GMP vs cGMP in Cleanrooms: What’s the Difference?
Top 5 Cleanroom Design Tips For Industrial Cleanrooms
One Pass Cleanroom vs. Recirculating Cleanroom
How to Select The Best Cleanroom Particle Counter
What Is An ISO-8 Cleanroom Classification?
5 Reasons to Purchase a Turnkey Complete Cleanroom
10 Tips on Choosing a Building for a Cleanroom
Building a Mask Manufacturing Cleanroom
Cleanroom Installation: What to Expect
What Are My Choices For Cleanroom Doors
Modular Cleanrooms vs. Standard Construction Cleanrooms
Modular vs. Softwall Cleanroom Systems
Eight Tips To Expedite Your Cleanroom Design Build
Quotes in 48 hours. Call or Complete Online RFQ Form.
American Cleanroom Systems® 2023 - Unauthorized use and/or duplication of this material without express and written permission from this website owner is strictly prohibited. Excerpts and links may be used, provided that full and clear credit is given to American Cleanrooms with appropriate and specific direction to the original content.